# Power Factor Correction in AC System

1. Real power (P) by which its unit is expressed in watts (W).

2. Reactive Power by which its unit is expressed in VAR

3. Apparent power (S) by which its unit is expressed in volt-amperes (VA).

The relationship of these three are represented by a power triangle.

In relation to this diagram we define power factor as the ratio of the real power to the apparent power, that is

The power drawn by the AC system depends on the connected loads whether those are purely resistive, inductive or capacitive. Purely resistive loads are drawn mostly by loads used in heating, passive resistor used in motor control starter and others.

But mostly if we consider the overall system particularly in industrial applications purely resistive system is very rare to exist. But before going further I would like to show first the graphical representation of power drawn by typical electrical system for more understanding.

**power factor = real power/ apparent power**

or we can expressed it as the cosine of the angle ( Ø ) of inclination from a geometrical perpective, that is

**power factor = cosine Ø**

**REACTIVE POWER WITH INDUCTIVE AND CAPACITIVE LOAD**The power drawn by the AC system depends on the connected loads whether those are purely resistive, inductive or capacitive. Purely resistive loads are drawn mostly by loads used in heating, passive resistor used in motor control starter and others.

But mostly if we consider the overall system particularly in industrial applications purely resistive system is very rare to exist. But before going further I would like to show first the graphical representation of power drawn by typical electrical system for more understanding.

**Inductive load**such as electric motors, lighting ballasts, welding machines and other equipments that has winding will draw inductive load.**Capacitive load**drawn mostly by a capacitor. There are also equipment like synchronous motor that draws leading power factor.

This diagram describes the power drawn by a typical electrical system. The positive angle represents capacitive system (leading power factor) while the negative angle represents inductive system (lagging power factor). In AC system the current and voltage are propagating as wave signals and the two quantities may or may not be displaced with each other. If they are displaced with each other, then either the voltage or the current will come first.

- If the current waveform comes first before the voltage, the current in this case leads the voltage by some degree of angle and this system will draw leading power.

However if we reverse the situation when the voltage comes first, the voltage in this case lags behind the current by some electrical degrees then that system is an inductive system and has lagging power factor.

Ideally the capacitor will draw purely leading current thus drawing purely leading power. This can be represented using the following vector diagram. Theoretically the current in this system leads the voltage by exactly 90 degrees

**THE POWER FACTOR CORRECTION USING A CAPACITOR**There are two methods where a system with low power factor can be corrected but I will discuss here the most commonly used method of power factor correction that is by way of installing a capacitor.

__Consider this example:__

A 3-phase, 440 volts electrical system is taking 10 MVA of power has an overall power factor of 0.6 lagging. Determine the rating of the capacitor in order to raise the power factor into .90?

- In this example we know can determine the power factor angle by simply taking the inverse cosine of the given power factor: Ø = (inv) cos (0.6) = -53.13 degrees. Therefore the vector diagram is represented as follows:

- The values were obtained using simple trigonometric calculation: P= 10 MVA x cos (-53.13 deg.) = 6 MW Q= 10 MVA x sin (-53.13 deg) = -8 MW

*Note: The negative quantity does not mean that it draws negative power, that is just a representation as a vector quantity. The negative value means the vector is directed downwards or below the X-axis.*

Refer to the above diagram we can conclude that we can have the same real power (P) but with different apparent power (S) and that values are dependent on the inductive power in the system.

Taking trigonometric calculation, we can get:

- By adding the capacitor that draws pure reactive power (+90 degrees) as shown in the highlighted vertical line, and take the vector addition using head-to-tail method, the new resultant apparent power is S (new) with Ø2 be the new power factor.
- The new power factor should have a value of 0.9 base on the requirement of the problem. And the new power factor angle must have a value of (inv) cosine (.9) = 25.84 electrical degrees.
- The degree of separation between the real power and the apparent power has obviously decreased from -53.13 electrical degrees to -25.84 electrical degrees.

Taking trigonometric calculation, we can get:

- Q (new) = 6 MW x tangent (25.84deg) = 2.9 MVAR S (new) = 6 MW/ cosine (25.84deg) = 6.67 MV.
- MVAR (added) = MVAR (old) - MVAR (new) = 8 MVAR - 2.9 MVAR = 5.1 MVAR
- Therefore we need a capacitor with a rating of 5.1 MVAR @ 440 VOLTS

- In real application these capacitors are divided into several steps with the use of power factor controller in order to prevent overshooting that will lead into a system with leading power factor.
- For example a design engineer decided to divide the 100 MVAR into 10 steps, that means he has to used a power factor controller with 10 discrete outputs and can control 10 magnetic contactors.
- And these contactors would serves as a magnetic switch directed to 10 capacitors.

Ideally the factor should be close to unity or 1.0 [cos 0 = 1.0] , that is the power factor angle is held to be zero. In this case the real power is equal to the apparent power thus making the system efficient. Sometimes the occurrence of the low power factor situation happened only during full blast operation of the plant.

**HOW POWER FACTOR AFFECTS THE SYSTEM.**

- Power factor correction can make our electrical system more efficient. Our electric meters operate according to the quantity of current that passes thru it.

P = V x I x pf -----> it follows that

I = P / [ V x pf ] ----> in order to minimize I then we should let pf closer to 1.0 (unless there are specific cases that make it technically not feasible).

**IMPORTANT THINGS TO CONSIDER**

- Before we correct our system power factor we have to know first the level of
__harmonics__of our system because as we know capacitors are sensitive to heating caused by harmonics. - We may need to undergo power quality audit first if we are suspecting a significant level of harmonics in our system.
- After determining the level of harmonics choose the type of capacitor that suits your need.
- The manufacturer or the supplier may provide you a whole unit where there are already capacitors, controllers and harmonic filters that is compatible to your system.

Thanks for educating us. Im sure repairmen are up to your blog for this information. I will saved this page as my bookmark too. If you need item for your project: Industrial Products Clark

ReplyDeleteI'd like to know how everything is going with this about HVAC company this topic thank for this

ReplyDeleteOn the off chance that another framework or frameworks are being thought of, it will be more financially savvy to plan for the decreased burden rather than the current burden. A couple of basic burden decrease systems include:

ReplyDeleteHVAC Blog

Get a gauge of how much the whole interaction will set you back. A few organizations might give you a modest gauge before the work is begun. In any case, whenever it is done you might be accused of extra expenses. https://www.wtfixair.com.au/

ReplyDeleteNote that the incredible greater part of homes have just one air return for each cooling framework. Sydney air conditioning services

ReplyDeleteThank you for your article post. Really thank you! Cool.HVAC Repair in Rowlett

ReplyDeleteThe best balance for seeking after a HVAC vocation can begin as ahead of schedule as senior secondary school. AC Repair Tampa

ReplyDeleteAn evaporative cooler enjoys a great deal of upper hands over a standard air conditoner in light of the fact that it has a lower cost of establishment, requires less support and works with less energy. Since they are more uncommon in certain pieces of the country, it appears as though a many individuals don't have a clue how an evaporative cooler functions. hydronic heating system

ReplyDeleteHVAC Services

The profound jewel and gold mines of South Africa use air conditioning to empower diggers to work in the thing would somehow be choking in heat, a large number of feet underneath the ground. With the air conditioning is associated with all aspects of the United States space program, from making rockets to following them through the climate. Beyond Heating And Cooling

ReplyDeleteDC link capacitors This particular is usually apparently essential and moreover outstanding truth along with for sure fair-minded and moreover admittedly useful My business is looking to find in advance designed for this specific useful stuffs…

ReplyDeleteThis is just the information I am finding everywhere. Thanks for your blog, I just subscribe your blog. This is a nice blog..

ReplyDeleteChimney Cleaning Aurora

We go out of our way to deliver world-class service. Contact us at any time with your queries. mini split hvac system

ReplyDeleteI read your post and got it quite informative. I couldn't find any knowledge on this matter prior to. I would like to thank you for sharing this article here. Read more about Best Air Conditioning Companies Sunshine Coast

ReplyDeleteThe best ac installers will likewise offer you a decent expense to get air conditioning introduced.

ReplyDeleteducted heating cost per hour

Air conditioning systems can be integrated with building management systems for centralized control.

ReplyDeleteair conditioning contractor Rockhampton