Motor Circuit Protection
Motor circuit protection describes the short-circuit protection of conductors supplying power to the motor, the motor controller, and motor control circuits/conductors. 430.52 provides the maximum sizes or settings for overcurrent devices protecting the motor branch circuit. A branch circuit is defined in Article 100 as “The circuit conductors between the final overcurrent device protecting the circuit and the outlet(s).”
Note that the branch circuit extends from the last branch circuit overcurrent device to the load. Table 430.52 lists the maximum sizes for Non-Time-Delay Fuses, Dual Element (Time-Delay) Fuses, Instantaneous Trip Circuit Breakers, and Inverse Time Circuit Breakers. Sizing is based on full load amp values shown in Table 430.247 through 430.250, not motor nameplate values. For example, the maximum time-delay fuse for a 10HP, 460 volt, 3 phase motor with a nameplate FLA of 13 amps would be based on 175% of 14 amps, not 175% of 13 amp.
Courtesy: Cooper Bussmann
- 430.52(C)(2) reminds the user that the maximum device ratings which are shown in a manufacturer’s overload relay table must not be exceeded even if higher values are allowed by other parts of 430.52.
- 430.52(C)(3) details the requirements that instant-trip CBs can only be used if part of a listed combination motor controller.