|Star Delta Power Circuit|
Star Delta starting is when the motor is connected (normally externally from the motor) in STAR during the starting sequence. When the motor has accelerated to close to the normal running speed, the motor is connected in DELTA.
The change of the external connection of the motor from Star to Delta is normally achieved by what is commonly referred to as Star-Delta starter. This starter is simply a number of contactors (switches) that connect the different leads together to form the required transition from Star to Delta.
When the motor is started in the star connection, the phase voltage of the motor is reduced by a factor of √3. The reductions in starting current, starting power, and starting torques for a reduced Voltage can each be calculated by using equation 1 (This ignores other factors like saturation, etc.):
These starters are normally set to a specific starting sequence, mostly using a time setting to switch between Star and Delta. There can be extensive protection on these starters, monitoring the starting time, current, Voltage, motor speed etc.
For example, if the supply voltage is 380 Volts. During starting in which the motor is connected into Star, the impressed voltage across each coil is 380/ 1.73 which is 220 Volts. As a result of the reduction of the impressed voltage, the starting torque will also reduce to 67%.
From the control circuit above, when switch S1 is pressed, there will be a complete path of electric current that will flow from L1 to L2 causing the following coils to be activated:
- K1 - line or main contactor
- K2 - star contactor
- K4 - timer (set at 3 to 5 seconds)
After the predetermined time, there will be a transition of timer contact. As such the time delay close contact (K3)which controls the star contactor will now become open while the time delay close contact (K2) will do the opposite. In this way, the transition from star to delta is executed.
The auxiliary contact of contactor K1 is connected in parallel with the start button S1 (latched) so that the circuit will remain activated even when S1 goes back to the open position. Note that S1 is characterized by a pushbutton that will return to its original state after being pressed.
The normally closed contacts K3 and K2 are also interlocked to prevent activating STAR and DELTA connection at the same time that can cause serious damage to the motor.
What are the advantages of using Star Delta starting?
The most significant advantage of this starting method is the reduction inrush current during starting. The reduction of the starting current can also reduce the mechanical stress of motor due to high starting torque. Note that when reduce voltage starting is not applied, the starting current could reach as high as 600%.